Maintenance method of
electric heating high pressure reactor :
1 working pressure and temperature operating in strict accordance with the product nameplate on the use of calibration, so as to avoid danger.
2 shall strictly comply with the provisions of the use of products in the specification on cooling, etc., do a good job of equipment maintenance and maintenance.
3 all valves should be used, should slow the rotation of the valve stem (needle), pressure tight cover, to achieve the sealing effect. At the time of closing, can not be too hard, so as not to damage the sealing surface.
4 control instruments should be operated by hand, and in accordance with the provisions set overload protection facilities.
5 should be installed in a rugged, flat on the table, the working table height according to the use of the situation to decide, equipment and the work station must be left around a certain space, so that the installation and maintenance of the late.
6 installed at the drive shaft and the vertical to the horizontal plane, the vertical inclination is not greater than the total height of equipment 1/1000
7 equipment itself in the process of taking over the parts, the reactor safety valve, must be equipped with the requirements of the reactor.
8 after installation to check the connection parts and transmission parts strong reliability, the connecting pipe, nozzle and seal air tightness test and machine to do, no bubble, dripping leaking.